220v baseboard heater wiring diagram - Collection of cadet baseboard heater wiring diagram you’ll be able to download totally free. Please down load those cadet baseboard heater wiring diagram series by the usage of the download button, or right click on selected photograph, then use save photo menu. Is 12/2 i used. The warmers are not wired together as you show. I ran twine from every heater to the thermostat container figuring on pigtailing the two warmers inside the electrical box. Can ido this?. Adequate, that is perfectly acceptable and isn't any trouble. The white and black that land on the breaker are the tstat l1 & l2 connections (line side of the tstat). On the tstat container, simply use a 6" (6 inch) pigtail of 12 awg white wire and combine to the two white load facet wires to (1) one 6" white wire and terminate to the t1 or t2 termination (load aspect heaters) at the stat. Repeat the equal pigtail method for the two black heater wires and connect to the t1 or t2 termination at the stat (load facet connection). Use one 6" black 12 awg for this pigtail. You ran the 2 heater cables as "home run" to the stat which is excellent as that is additionally a parallel connection. The opposite alternative as shown in my diagram is to daisy chain the 2 warmers together which is also a parallel connection. Each wiring strategies are adequate. Your wiring parallels the warmers on the stat, my diagram parallels the wires at the heaters. Name is ***** ***** i can be glad to assist you along with your electric question. My aim is to exceed your expectancies on simply answer! 1) baseboard warmers need to be wired in parallel with each together and then linked to the tstat. The l1 & l2 connection are the line side connections and those are the 2 wires that originate from the breaker. The t1 & t2 are the 2 wires that increase out to the paralleled heater wiring (load aspect connection). 2) test the diagram proven under. Is this how you have got related the wires? Since you are using black and purple wires, my diagram shows white and black, however the same principle, just a unique colour. Purple and black can be used in my diagram. Just alternative the white for a crimson. Three) what twine hues land at the double pole breaker? Black & pink or black & white? Four) 12/three is not required as you may have used 12/2 romex. A 240 volt baseboard heater best calls for 2 hot conductors. Just cap off the white wires at both ends in case you are using black/pink. !.