Posts index: a b c d e f g h i j okay l m n o p q r s t u v w x y z zero 1 2 3 four 5 6 7 8 nine pictures index: a b c d e f g h i j ok l m n o p q r s t u v w x y z zero 1 2 3 4 5 6 7 8 nine. A 5" long brown twine inside the cord harness at the low fireplace strain transfer presents 24 vac humidifier control. This cord is powered any time the stress transfer is closed. To connect 24 vac hum, join the 24 vac line of the humidifier to the 5" brown wire. The connection may be made by both stripping the wire and the usage of a twine nut or by way of the use of a subject supplied quick join terminal. The wiring must conform to all local and national codes. Join the com aspect of the humidifier to the c terminal on the furnace manipulate board (or to the com aspect of the 24 vac transformer). Do now not join 115v humidifier to those terminals.
Bought a dual fuel goodman machine with ctk04 comfortnet thermostat. The thermostat installtion manual indicates wiring of a humidifier to the (2) hum terminals on the furnace ifc. My furnace version is a comfornet like minded model gmvc950905dx. It can't locate (2)hum terminals at the ifc. Are they re-purposing a number of the legacy terminals for the non comfornet communicating thermostat with out telling me?.